The GSM-GPRS remote IO module has two digital “dry contact” inputs, two analog inputs with 0-10V range and two analog inputs with 0-10V or 0-20mA range. The customer sets the mode of analog inputs via the GUI.
The device supports 1-Wire and RS-485 (MODBUS RTU) interfaces. Both interfaces can carry up to 8 sensors, shared between the two interfaces in a random ratio.
The device records all monitored parameters in internal FLASH memory. The records are made on the previous set time interval and/or on an alarm condition. The log file can be periodically uploaded to a dedicated server by HTTP Post.
TCG140 can initiate a connection (HTTP Post) to remote dedicated servers. The payload of this post is XML file, with current values of monitored parameters. The HTTP Post can be sent periodically or under alarm conditions. As an answer to the HTTP Post, an HTTP API command can be returned for relay activation or change of some settings.
In addition to the HTTP Post alert, the device can send SMS and/or e-mail as an extra alert for up to 5 SMS and e-mails recipients.
- Quad-bands GSM connectivity;
- Setup via USB (Windows setup program) or SMS;
- 2 digital ”dry contact” inputs;
- 1-Wire interface for up to 8 Teracom sensors;
- RS-485 interface for up to 8 MODBUS RTU sensors;
- 2 analog inputs with 0-10VDC range;
- 2 analog inputs with 0-10VDC or 0-20mA mode (WEB control);
- 4 relay outputs with NO and NC contacts;
- Data logger for up to 52000 records;
- Periodical upload of data logger file to a remote HTTP server;
- HTTP Post – XML data is sent pereodicaly to a remote HTTP server;
- HTTP API commands;
- SMS alarm alerts (up to 5 numbers);
- Email alarm alerts (up to 5 email recipients), SMTP with TLS support;
- Single call control for the relays from up to 5 numbers;
- Firmware update over USB or GPRS.
- Humidity, temperature and CO2 monitoring;
- Mobile envinromental monitoring for vechicles;
- Street lighting control for smart cities systems;
- Data logging of industrial processes;
- Remote water pupm station monitoring;
- Drug and food facilities monitoring.